The cooler element, in high resistance aluminium alloy, is obtained by means of a braze-welding process carried out under vacuum.
Each data sheet provides the technical information about the heat exchanger used for cooling oil hydraulic system and about fans operated by electric or hydraulic motor.
Core’s technical specification
Please contact HYDRAPAC ITALIA for aggressive ambient
The heat exchanger should be installed in such a way that there should be no obstacles to the air flow, respecting the minimum distance from the wall (1/2 fan diameter) so as to ensure a natural flow of cooling air.
The cooler can be fitted in vertical and horizontal position.
RAL series coolers are normally used for cooling hydraulic circuits and installed on the return lines: they must be protected from impact and mechanical vibrations by support and must be connected to the circuit with flexible pipes. To prevent any damage caused by changes in flow, hammering and pulsations we recommend installing a by-pass valve
For other fluid consuls HYDRAPAC ITALIA
Cleaning oil side
After having dismantled the exchanger, carry out the cleaning procedure by circulating de-greasing substance inside the radiator compatible with steel. Wash with hydraulic oil before reconnecting the cooler.
Cleaning air side
Carry out this procedure using compressed air. Make sure that the direction of the jet is parallel to the fins so that they are not damaged. If the blockage of the exchanger is caused by build up of oil or grease, c1eaning can be carried out using a jet of steam or hot water. During c1eaning procedures the electric motor must be adequately protected.
During operation of heat exchangers observe following instructions:
©2017 Hydrapac Italia S.r.l
Vicolo del lavoro, 9 40069 Zola Predosa (BO) Italy
Phone: +39 051 755082 - Fax +39 051 6185568
C.F. e P.IVA: IT 02423401203 - R.E.A. 438331
Share capital 10.000,00 i.v.